SR Electrical Services LTD attended the Ulverston Depot due to a breakdown with the sites tank gauging system.
After further investigation, it was determined that the existing tank gauging system was obsolete; meaning we were unable to source replacement parts for the system.
Due to this, our team designed and measured the existing tank to allow for probes to be made to the site's perisic tank's diameter size and product type. We have now installed 3 number Veeder Root Magflex Probes, and 3 number Mag1 probes onsite. We have also installed a new Veeder Root Approved blue IS cable tray.
SR Electrical have supplied and installed a TLS450 PLUS unit onsite, with a remote DISS 200 unit for drivers' access and to provide off-loading facility checking for Bridger drivers. As well as these areas of work, we have also supplied and installed an overfill protection sounder / beacons in various locations onsite.
Certas Energy have allowed SR Electrical Services to install our remote cloud monitoring equipment into the tank gauging system to allow for wet stock management and maintenance to be carried out when the site's gauge is in operation.
Latest NewsView all
4 Signs Your Business is due a Hazardous Area Electrical Inspection
With the vast amount of directives and regulations surrounding hazardous areas, it can be easy to forget the importance of ensuring that the electrics within this area are safe.
Read more Share
The Essentials of Electrical Control Panels and Why You Need One
You may be thinking, control panels, how would they benefit my business? Well, we can tell you that they are widely used in industrial, commercial, and residential applications and are essential for industrial automation.
Read more Share
Latest ProjectsView all
Header Point Lighting Rectification
Our team carried out a rectification project on faulty header point light fittings in Lerwick.
Additional Replacement Light Fitting
In December 2020, our team undertook rectification of a hazardous area light fitting in Northiam.