SR Electrical Services LTD attended the Ulverston Depot due to a breakdown with the site's tank gauging system. Discover how we helped here.
Site/Location: Ulverston Depot
Type of Works: Tank Gauging Installation
Client: Certas Energy UK LTD
SR Electrical Services LTD attended the Ulverston Depot due to a breakdown with the site's tank gauging system. After further investigation, it was determined that the existing tank gauging system was obsolete; meaning we were unable to source replacement parts for the system.
Due to this, our team designed and measured the existing tank to allow for probes to be made to the site's perisic tank's diameter size and product type. We have now installed 3 number Veeder Root Magflex Probes, and 3 number Mag1 probes onsite. We have also installed a new Veeder Root Approved blue IS cable tray.
SR Electrical have supplied and installed a TLS450 PLUS unit onsite, with a remote DISS 200 unit for drivers' access and to provide off-loading facility checking for Bridger drivers. As well as these areas of work, we have also supplied and installed an overfill protection sounder / beacons in various locations onsite.
Certas Energy have allowed SR Electrical Services to install our remote cloud monitoring equipment into the tank gauging system to allow for wet stock management and maintenance to be carried out when the site's gauge is in operation.
Latest NewsView all
Out with the old, in with the new
2020 has been a strange year. Here SR Electrical Services LTD, we would like to say thank you to each and every one of our valued clients and dedicated team members for their continued support and hard work throughout the year. We are extremely grateful.
Read more Share
Is my workplace at risk of a combustible dust explosion?
Discover how our team can help keep your workplace, teams, and visitors safe from combustible dust explosions.
Read more Share
Latest ProjectsView all
Tank Gauging Installation - Wales
Recently, the SR Electrical Services LTD team were required to make a journey to Wales in order to help a site with their 2No temporary 1 Arm loading skids installation.
Rectification Hazardous Area Electrical Defects
Electrical Inspection and Test of the Oil Lubricant control panels and electrical installation