We supplied and installed a new distribution board to a client in Alconbury
Our team investigated constant tripping of electrics on-site in Alconbury. Upon carrying out our investigations, we identified that the site had a common 30mA RCD in mains distribution board which did not comply and was causing intermittent power outage/nuisance tripping when an increase of current passed through the site, i.e. when 3 or 4 pumps were running simultaneously.
We were asked to provide a solution which would resolve the issue for our client and prevent unnecessary disruptions to site.
So this meant that we supplied and installed a compliant distribution board complete with individual 30mA RCD protection and double pole isolation to tank dispensers, control systems and local dispenser lighting. This has rectified the issue and the client is happy to now be running back at full capacity.
Latest NewsView all
4 Signs Your Business is due a Hazardous Area Electrical Inspection
With the vast amount of directives and regulations surrounding hazardous areas, it can be easy to forget the importance of ensuring that the electrics within this area are safe.
Read more Share
The Essentials of Electrical Control Panels and Why You Need One
You may be thinking, control panels, how would they benefit my business? Well, we can tell you that they are widely used in industrial, commercial, and residential applications and are essential for industrial automation.
Read more Share
Latest ProjectsView all
Header Point Lighting Rectification
Our team carried out a rectification project on faulty header point light fittings in Lerwick.
Additional Replacement Light Fitting
In December 2020, our team undertook rectification of a hazardous area light fitting in Northiam.