We carried out an electrical replacements project due to badly corroded terminals and connections.
The SR Electrical team were shocked to find that the cause of a defect found during the inspection at Fort William was due to the j-box being full of water, which had consequently corroded the terminals and connections.
We were able to replace this with a new j-box, and reconnected the cables. The team were also able to carry out the works on the same day, once approved by the regional transport manager for Scotland.
If you would like to find out more about our electrical inspection services and how they could help your business' workplace, click here. Alternatively, if you would like to speak to a member of our friendly team of experts, click here.
Latest NewsView all
4 Signs Your Business is due a Hazardous Area Electrical Inspection
With the vast amount of directives and regulations surrounding hazardous areas, it can be easy to forget the importance of ensuring that the electrics within this area are safe.
Read more Share
The Essentials of Electrical Control Panels and Why You Need One
You may be thinking, control panels, how would they benefit my business? Well, we can tell you that they are widely used in industrial, commercial, and residential applications and are essential for industrial automation.
Read more Share
Latest ProjectsView all
Header Point Lighting Rectification
Our team carried out a rectification project on faulty header point light fittings in Lerwick.
Additional Replacement Light Fitting
In December 2020, our team undertook rectification of a hazardous area light fitting in Northiam.